Now with 3 locations
24hr Emergency Service
Professional Duct Cleaning
Residential & Commercial
Call Us Today For A Free Estimate!
Commonly Reported HVAC Problems:
Commonly Reported HVAC Problems:
[Copyright © 1996-2014. Hannabery HVAC. All rights reserved.]
Water leak at indoor unit:
Under no circumstances should you ever see water around the indoor unit. This is a sign that something is either dripping, leaking, or not draining. But don't panic, sometimes it can be a very minor problem.
In the cooling mode, the indoor evaporator coil and the suction line (the large copper refrigerant line in black insulation) sweats. That is part of the purpose of the black insulation (armaflex), to keep the condensation from dripping. Sometimes if the insulation is missing or if it has open seems, it can cause dripping and obviously this is an easy fix. All armaflex joints should be butted-up tight and well taped.
The evaporator produces a lot of condensation (water) during the summer, which runs down the coil into a pan, then out to the drain. The drain goes either into the ground, outside the house, or into a condensate pump. Then in turn, the pump takes the water either outside the house or into a plumbing drain. If the coil is dirty, then the water, instead of running down the coil, will hit the dirt, then drip onto the floor. This is one reason why the coil should be cleaned annually, not to mention for efficiency reasons.
Now if the coil is dirty, the water will mix with the dirt and the dirt will end up in the pan, and it will end up in the drain, the drain trap, and anywhere else it can cause a problem. The bottom of the trap is the most common source of a clog and it can be cleaned out with a long flexible cleaning brush and flushing water down the cleanout cap. Keep in mind, it doesn't take much dirt to clog a drain.
And if your unit is in an attic or a finished basement, this can cause terrible damage. This is another reason why it is important to always have a good, clean, properly sized air filter, along with having annual inspections.
Sometimes the indoor coil can actually ice-up. And when the ice eventually melts, it drips onto the floor. Like water, you should never see ice anywhere on your system during the cooling season.
Furnace Leaking, Humidifier Leaking...
So keep your eyes open. If you see water, try to trace where it is coming from. Sometimes it is a simple fix. Sometimes not.
Below is a list of possible causes. Items in red usually require a service call. Items in blue however can be addressed, some even fixed by the homeowner.
Red = Professional fix | Blue = Homeowner fix
The bottom causes in blue are commonly found problems and can be addressed by the homeowner. Try to check for these conditions first before calling for service.
Please keep in mind that the information found on our website is provided free of charge and Hannabery HVAC does not assume any liability resulting from the information we provide. We hope this information helps, but please note that these are just rough guidelines, and not all possible situations are covered. Your HVAC system should be inspected and repaired by a trained technician.
How Comfortable Do You Want To Be?
Call us at 1-800-544-HEAT
[Must be in our service area]
Forced Hot Air Furnaces: Troubleshooting & Repair
By Roger Vizi
Audel HVAC Fundamentals, Heating Systems...
By James E. Brumbaugh
System Diagnostics and Troubleshooting Procedures
By John Tomczyk
Study Guide for Modern Refrigeration and Air...
By Andrew D. Althouse,...
Malco TC312 Tube Cutter for Tubing 1/4-Inch-1 5/8-Inch Outside Diameter
Includes spare cutting wheel
Electronic Thermometer, -40 C to 232 C, -40 F to 450 F
Includes protective sheath, clip, and battery
Klein HD2000-9NE High-Leverage Side-Cutting Pliers
Usually ships in 24 hours
Milwaukee 6509-22 Sawzall 11-Amp Reciprocating Saw
Includes 1 blade and case
Main Office: 200 Schantz Road, Allentown, PA 18104
PA CONTRACTOR #8215
With 3 locations to serve you better!
Copyright © 1996-2014. Hannabery HVAC. All rights reserved.