Now with 3 locations
24hr Emergency Service
Professional Duct Cleaning
Residential & Commercial
Call Us Today For A Free Estimate!
Commonly Reported HVAC Problems:
Commonly Reported HVAC Problems:
[Copyright © 1996-2014. Hannabery HVAC. All rights reserved.]
Circuit breaker keeps tripping:
If the circuit breaker to your indoor or outdoor unit trips, you may reset it. Turn it to the "off" position if it isn't there already, then back to the "on" position. If the breaker trips a second time, then you should schedule a service call.
The breaker is tripping for a reason. It is protecting the equipment, the wiring, and the house. Do not just keep resetting it and ignoring the situation. Yes, it is possible that maybe it is just a bad breaker or maybe it was just a thunderstorm. But you are dealing with high voltage and amperage, and possibly high temperatures, which could cause wires to melt, possibly starting a fire.
Loose Electrical Connections...
One very common cause for breakers to trip is loose electrical connections. Larger aluminum wires especially, tend to expand and contract with the weather, causing the connections to loosen over time. It is just a matter of tightening the connections. * Use extreme caution, High Voltage!
Another common cause is a direct electrical short in the wiring or equipment. This is identified by the breaker tripping instantly, once the unit attempts to start. In this situation, do not even try to reset the breaker again. Call for service immediately.
Sometimes the breaker for the outdoor unit trips because the compressor is having trouble starting. The compressor could be old, weak or just tight and a "hard start kit" (installed by a service technician) might do the job getting it going again. Or it may be as simple as replacing a bad capacitor which helps start the compressor.
Below is a list of possible causes. Items in red usually require a service call. Items in blue however can be addressed, some even fixed by the homeowner.
Red = Professional fix | Blue = Homeowner fix
The bottom causes in blue are commonly found problems and can be addressed by the homeowner. Try to check for these conditions first before calling for service.
Note - A circuit breaker should never feel hot to the touch. You can touch the breaker by using the backs of your fingers. The breaker should feel room temperature or warm. If it is hot, this could indicate a problem. Do not ignore it!
Please keep in mind that the information found on our website is provided free of charge and Hannabery HVAC does not assume any liability resulting from the information we provide. We hope this information helps, but please note that these are just rough guidelines, and not all possible situations are covered. Your HVAC system should be inspected and repaired by a trained technician.
How Comfortable Do You Want To Be?
Call us at 1-800-544-HEAT
[Must be in our service area]
Forced Hot Air Furnaces: Troubleshooting & Repair
By Roger Vizi
Audel HVAC Fundamentals, Heating Systems...
By James E. Brumbaugh
System Diagnostics and Troubleshooting Procedures
By John Tomczyk
Study Guide for Modern Refrigeration and Air...
By Andrew D. Althouse,...
Malco TC312 Tube Cutter for Tubing 1/4-Inch-1 5/8-Inch Outside Diameter
Includes spare cutting wheel
Electronic Thermometer, -40 C to 232 C, -40 F to 450 F
Includes protective sheath, clip, and battery
Klein HD2000-9NE High-Leverage Side-Cutting Pliers
Usually ships in 24 hours
Milwaukee 6509-22 Sawzall 11-Amp Reciprocating Saw
Includes 1 blade and case
Main Office: 200 Schantz Road, Allentown, PA 18104
PA CONTRACTOR #8215
With 3 locations to serve you better!
Copyright © 1996-2014. Hannabery HVAC. All rights reserved.