Now with 3 locations
24hr Emergency Service
Professional Duct Cleaning
Residential & Commercial
Call Us Today For A Free Estimate!
Commonly Reported HVAC Problems:
[Copyright © 1996-2013. Hannabery HVAC. All rights reserved.]
Heat pump never quite reaches temperature:
In the Heating Mode:
In other words... if you set your thermostat for 71 degrees in the winter and your house only seems to get up to 69 degrees. This problem/situation is very common and it generates many service calls. And sometimes this is caused by a genuine problem, but unfortunately, in extremely cold weather, even a properly working heat pump may have trouble maintaining desired temperature.
Why is this? When it gets below a certain temperature, in our area - around 35 degrees, a heat pump loses efficiency and cannot keep up with the heat loss of the structure. When the temperature in the house drops approximately 2 degrees below room temperature, supplemental heat comes on to assist the heat pump (usually in the form of electric resistance heaters). When it gets to within 1.5 degrees of room temperature, the back-up heat cycles off and the heat pump continues running; trying to reach temperature, but cannot. This usually happens when the temperature is at it's coldest - 0 to 30 degrees.
This is however, the way heat pumps are designed to operate. Even though they don't put out a lot of heat into the house, and they run for long periods of time, they are still quite efficient.
So, if it is very cold out and you desire your house to be a certain temperature, you might have to raise your thermostat by 2 degrees to maintain it. Now, if it isn't extremely cold out (above 35 degrees), and your heat pump is not maintaining temperature, this indicates a problem!
Below is a list of possible causes. Items in red usually require a service call. Items in blue however can be addressed, some even fixed by the homeowner.
Red = Professional fix | Blue = Homeowner fix
The bottom five causes in blue are commonly found problems and can be addressed by the homeowner.
Here is a checklist to go through before requesting a service call:
If not reaching temperature in the Cooling Mode, please see:
Please keep in mind that the information found on our website is provided free of charge and Hannabery HVAC does not assume any liability resulting from the information we provide. We hope this information helps, but please note that these are just rough guidelines, and not all possible situations are covered. Your HVAC system should be inspected and repaired by a trained technician.
How Comfortable Do You Want To Be?
Call us at 1-800-544-HEAT
[Must be in our service area]
The HVAC Store
General-Aire Wheel - Complete With Pad, Rod & Retaining Clip
Fits Model 81 Humidifier
Aprilaire Humidifier Water Panel: Stock #35
Fits Models: 350, 360, 560, 560A, 600, 700, 760, 760A
Aprilaire/Space-Gard Air Cleaner Stock #201 Media Replacements:
Fits Models: 2200, 2250
Aprilaire/Space-Gard Air Cleaner Stock #401 Media Replacements:
Fits Models: 2400
Forced Hot Air Furnaces: Troubleshooting & Repair
By Roger Vizi
Audel HVAC Fundamentals, Heating Systems...
By James E. Brumbaugh
System Diagnostics and Troubleshooting Procedures
By John Tomczyk
Study Guide for Modern Refrigeration and Air...
By Andrew D. Althouse,...
Malco TC312 Tube Cutter for Tubing 1/4-Inch-1 5/8-Inch Outside Diameter
Includes spare cutting wheel
Electronic Thermometer, -40 C to 232 C, -40 F to 450 F
Includes protective sheath, clip, and battery
Klein HD2000-9NE High-Leverage Side-Cutting Pliers
Usually ships in 24 hours
Milwaukee 6509-22 Sawzall 11-Amp Reciprocating Saw
Includes 1 blade and case
Main Office: 200 Schantz Road, Allentown, PA 18104
PA CONTRACTOR #8215
With 3 locations to serve you better!
Website design by firstname.lastname@example.org
Copyright © 1996-2013. Hannabery HVAC. All rights reserved.