Commonly Reported HVAC Problems:
Copyright © 1997 Hannabery HVAC. All rights reserved.
Thermostat red light flashing or stays on:
When the thermostat light (Emergency Heat Light) is flashing or on during normal operation (whether in the cooling or the heating mode, but not the Emergency Heat mode), this usually indicates that the outdoor unit is "locked-out". This means the outdoor unit has shut itself off because of a problem, and it sends a signal to the thermostat, letting you know that there is a problem.
When this happens, the indoor unit tends to keep on running because the indoor unit doesn't know there is a problem. And if the outdoor unit isn't running, the indoor unit will most likely never satisfy the thermostat; it will just keep running and running and running.
Many systems, like the York Stellar Series units have a diagnostic feature. When you see the light flashing, it flashes a code. You can count the number of flashes, usually between two and nine, and then it just repeats itself. You can then reset the system by turning the thermostat "off", waiting thirty seconds then turning it back
on again. This should restart the system, but it may take up to 10 minutes for the outdoor unit to start up.
Some systems require shutting the power to the indoor unit off momentarily, then back on. The light should also go out. After 10 minutes, see if the outdoor unit is running. If the light doesn't go out or if the unit doesn't start, you may need to call for service, assuming you checked for the obvious; like tripped breakers or the outdoor reset button.
Sometimes a unit will "lock-out" on a fluke or a weather-related condition, and resetting it will solve the problem. But if the unit "locks-out" again, most likely there is a problem and you should schedule a service-call.
Below is a list of possible causes. Items in red usually require a service call. Items in blue however can be addressed, some even fixed by the homeowner.
Red = Professional fix | Blue = Homeowner fix
York Stellar Series Flash Code:
- 2 code- off on high pressure
- 3 code- off on high discharge temperature
- 4 code- off on low discharge temperature
- 5 code- default defrost, defrosting too often
- 7 code- bad ambient sensor
- 8 code- bad liquid-line sensor
Other Heat Pump Systems:
- High pressure or high temperature switch open
- Low pressure or low temperature switch open
- Defrosting too much
- High pressure switch open - some units have a manual reset button located on the outdoor unit - possible cause: blocked air filter or coil, bad fan motor, overcharge, running heat on a hot day, stuck contactor in heating mode
- Defrosting too much (weather conditions related) - possible cause: outdoor unit in a snow-drift or covered in ice.
Please keep in mind that the information found on our website is provided free of charge and Hannabery HVAC does not assume any liability resulting from the information we provide. We hope this information helps, but please note that these are just rough guidelines, and not all possible situations are covered. Your HVAC system should be inspected and repaired by a trained technician.
How Comfortable Do You Want To Be?
Call us at 1-800-544-4328
[Must be in our service area]